Worldmap highlighting oceanic regions with high temperature gradients (between surface and 1000m depth)
OTEC diagram and applications

Ocean Thermal Energy Conversion (OTEC) uses the ocean thermal gradient between cooler deep and warmer shallow or surface seawaters to run a heat engine and produce useful work, usually in the form of electricity. OTEC can operate with a very high capacity factor and so can operate in base load mode.

The denser cold water masses, formed by ocean surface water interaction with cold atmosphere in quite specific areas of the North Atlantic and the Southern Ocean, sink into the deep sea basins and spread in entire deep ocean by the thermohaline circulation. Upwelling of cold water from the deep ocean is replenished by the downwelling of cold surface sea water.

Among ocean energy sources, OTEC is one of the continuously available renewable energy resources that could contribute to base-load power supply.[1] The resource potential for OTEC is considered to be much larger than for other ocean energy forms.[2] Up to 88,000 TWh/yr of power could be generated from OTEC without affecting the ocean's thermal structure.[3]

Systems may be either closed-cycle or open-cycle. Closed-cycle OTEC uses working fluids that are typically thought of as refrigerants such as ammonia or R-134a. These fluids have low boiling points, and are therefore suitable for powering the system's generator to generate electricity. The most commonly used heat cycle for OTEC to date is the Rankine cycle, using a low-pressure turbine. Open-cycle engines use vapor from the seawater itself as the working fluid.

OTEC can also supply quantities of cold water as a by-product. This can be used for air conditioning and refrigeration and the nutrient-rich deep ocean water can feed biological technologies. Another by-product is fresh water distilled from the sea.[4]

OTEC theory was first developed in the 1880s and the first bench size demonstration model was constructed in 1926. Currently operating pilot-scale OTEC plants are located in Japan, overseen by Saga University, and Makai in Hawaii.[5]

## History

Attempts to develop and refine OTEC technology started in the 1880s. In 1881, Jacques Arsene d'Arsonval, a French physicist, proposed tapping the thermal energy of the ocean. D'Arsonval's student, Georges Claude, built the first OTEC plant, in Matanzas, Cuba in 1930.[6][7] The system generated 22 kW of electricity with a low-pressure turbine.[8] The plant was later destroyed in a storm.[9]

In 1935, Claude constructed a plant aboard a 10,000-ton cargo vessel moored off the coast of Brazil. Weather and waves destroyed it before it could generate net power.[8] (Net power is the amount of power generated after subtracting power needed to run the system).

In 1956, French scientists designed a 3 MW plant for Abidjan, Ivory Coast. The plant was never completed, because new finds of large amounts of cheap petroleum made it uneconomical.[8]

In 1962, J. Hilbert Anderson and James H. Anderson, Jr. focused on increasing component efficiency. They patented their new "closed cycle" design in 1967.[10] This design improved upon the original closed-cycle Rankine system, and included this in an outline for a plant that would produce power at lower cost than oil or coal. At the time, however, their research garnered little attention since coal and nuclear were considered the future of energy.[9]

Japan is a major contributor to the development of OTEC technology.[11] Beginning in 1970 the Tokyo Electric Power Company successfully built and deployed a 100 kW closed-cycle OTEC plant on the island of Nauru.[11] The plant became operational on 14 October 1981, producing about 120 kW of electricity; 90 kW was used to power the plant and the remaining electricity was used to power a school and other places.[8] This set a world record for power output from an OTEC system where the power was sent to a real (as opposed to an experimental) power grid.[12] 1981 also saw a major development in OTEC technology when Russian engineer, Dr. Alexander Kalina, used a mixture of ammonia and water to produce electricity. This new ammonia-water mixture greatly improved the efficiency of the power cycle. In 1994 Saga University designed and constructed a 4.5 kW plant for the purpose of testing a newly invented Uehara cycle, also named after its inventor Haruo Uehara. This cycle included absorption and extraction processes that allow this system to outperform the Kalina cycle by 1-2%.[13] Currently, the Institute of Ocean Energy, Saga University, is the leader in OTEC power plant research and also focuses on many of the technology's secondary benefits.

### Hainan

On April 13, 2013, Lockheed contracted with the Reignwood Group to build a 10 megawatt plant off the coast of southern China to provide power for a planned resort on Hainan island.[65] A plant of that size would power several thousand homes.[66][67] The Reignwood Group acquired Opus Offshore in 2011 which forms its Reignwood Ocean Engineering division which also is engaged in development of deepwater drilling.[68]

### Japan

Currently the only continuously operating OTEC system is located in Okinawa Prefecture, Japan. The Governmental support, local community support, and advanced research carried out by Saga University were key for the contractors, IHI Plant Construction Co. Ltd, Yokogawa Electric Corporation, and Xenesys Inc, to succeed with this project. Work is being conducted to develop a 1MW facility on Kume Island requiring new pipelines. In July 2014, more than 50 members formed the Global Ocean reSource and Energy Association (GOSEA) an international organization formed to promote the development of the Kumejima Model and work towards the installation of larger deep seawater pipelines and a 1MW OTEC Facility.[69] The companies involved in the current OTEC projects, along with other interested parties have developed plans for offshore OTEC systems as well.[70] - For more details, see "Currently Operating OTEC Plants" above.

### United States Virgin Islands

On March 5, 2014, Ocean Thermal Energy Corporation (OTEC)[71] and the 30th Legislature of the United States Virgin Islands (USVI) signed a Memorandum of Understanding to move forward with a study to evaluate the feasibility and potential benefits to the USVI of installing on-shore Ocean Thermal Energy Conversion (OTEC) renewable energy power plants and Seawater Air Conditioning (SWAC) facilities.[72] The benefits to be assessed in the USVI study include both the baseload (24/7) clean electricity generated by OTEC, as well as the various related products associated with OTEC and SWAC, including abundant fresh drinking water, energy-saving air conditioning, sustainable aquaculture and mariculture, and agricultural enhancement projects for the Islands of St Thomas and St Croix.[73]

On July 18, 2016, OTE's application to be a Qualifying Facility was approved by the Virgin Islands Public Services Commission.[32] OTE also received permission to begin negotiating contracts associated with this project.[33]

### Kiribati

South Korea's Research Institute of Ships and Ocean Engineering (KRISO) received Approval in Principal from Bureau Veritas for their 1MW offshore OTEC design. No timeline was given for the project which will be located 6 km offshore of the Republic of Kiribati.[74]

### Martinique

Akuo Energy and DCNS were awarded NER300 funding on July 8, 2014[75] for their NEMO (New Energy for Martinique and Overseas) project which is expected to be a 10.7MW-net offshore facility completed in 2020.[76] The award to help with development totaled 72 million Euro.[77]

### Maldives

On February 16, 2018, Global OTEC Resources announced plans[78] to build a 150 kW plant in the Maldives, designed bespoke for hotels and resorts.[79] "All these resorts draw their power from diesel generators. Moreover, some individual resorts consume 7,000 litres of diesel a day to meet demands which equates to over 6,000 tonnes of CO2 annually," said Director Dan Grech.[80] The EU awarded a grant and Global OTEC resources launched a crowdfunding campaign for the rest.[78]

## Related activities

OTEC has uses other than power production.

### Desalination

Desalinated water can be produced in open- or hybrid-cycle plants using surface condensers to turn evaporated seawater into potable water. System analysis indicates that a 2-megawatt plant could produce about 4,300 cubic metres (150,000 cu ft) of desalinated water each day.[81] Another system patented by Richard Bailey creates condensate water by regulating deep ocean water flow through surface condensers correlating with fluctuating dew-point temperatures.[82] This condensation system uses no incremental energy and has no moving parts.

On March 22, 2015, Saga University opened a Flash-type desalination demonstration facility on Kumejima.[83] This satellite of their Institute of Ocean Energy uses post-OTEC deep seawater from the Okinawa OTEC Demonstration Facility and raw surface seawater to produce desalinated water. Air is extracted from the closed system with a vacuum pump. When raw sea water is pumped into the flash chamber it boils, allowing pure steam to rise and the salt and remaining seawater to be removed. The steam is returned to liquid in a heat exchanger with cold post-OTEC deep seawater.[84] The desalinated water can be used in hydrogen production or drinking water (if minerals are added).

### Hydrogen production

Hydrogen can be produced via electrolysis using OTEC electricity. Generated steam with electrolyte compounds added to improve efficiency is a relatively pure medium for hydrogen production. OTEC can be scaled to generate large quantities of hydrogen. The main challenge is cost relative to other energy sources and fuels.[91]

### Mineral extraction

The ocean contains 57 trace elements in salts and other forms and dissolved in solution. In the past, most economic analyses concluded that mining the ocean for trace elements would be unprofitable, in part because of the energy required to pump the water. Mining generally targets minerals that occur in high concentrations, and can be extracted easily, such as magnesium. With OTEC plants supplying water, the only cost is for extraction.[92] The Japanese investigated the possibility of extracting uranium and found developments in other technologies (especially materials sciences) were improving the prospects.[93]

### Climate control

Ocean thermal gradient can be used to enhance rainfall and moderate the high ambient summer temperatures in tropics to benefit enormously the mankind and the flora and fauna.[citation needed] When sea surface temperatures are relatively high on an area, lower atmospheric pressure area is formed compared to atmospheric pressure prevailing on the nearby land mass inducing winds from the landmass towards the ocean. Oceanward winds are dry and warm which would not contribute to good rainfall on the landmass compared to landward moist winds. For adequate rainfall and comfortable summer ambient temperatures (below 35 °C) on the landmass, it is preferred to have landward moist winds from the ocean. Creating high pressure zones by artificial upwelling on sea area selectively can also be used to deflect / guide the normal monsoon global winds towards the landmass. Artificial upwelling of nutrient-rich deep ocean water to the surface also enhances fisheries growth in areas with tropical and temperate weather.[94] It would also lead to enhanced carbon sequestration by the oceans from improved algae growth and mass gain by glaciers from the extra snow fall mitigating sea level rise or global warming process.[citation needed] Tropical cyclones also do not pass through the high pressure zones as they intensify by gaining energy from the warm surface waters of the sea.

The cold deep sea water (<10 °C) is pumped to the sea surface area to suppress the sea surface temperature (>26 °C) by artificial means using electricity produced by mega scale floating wind turbine plants on the deep sea. The lower sea water surface temperature would enhance the local ambient pressure so that atmospheric landward winds are created. For upwelling the cold sea water, a stationary hydraulically driven propeller (≈50 m diameter) is located on the deep sea floor at 500 to 1000 m depth with a flexible draft tube extending up to the sea surface. The draft tube is anchored to the sea bed at its bottom side and top side to floating pontoons at the sea surface. The flexible draft tube would not collapse as its inside pressure is more compared to outside pressure when the colder water is pumped to the sea surface. Middle east, north east Africa, Indian subcontinent and Australia can get relief from hot and dry weather in summer season, also prone to erratic rainfall, by pumping deep sea water to the sea surface from the Persian gulf, Red sea, Indian Ocean and Pacific Ocean respectively.[citation needed]

## Thermodynamics

A rigorous treatment of OTEC reveals that a 20 °C temperature difference will provide as much energy as a hydroelectric plant with 34 m head for the same volume of water flow.[citation needed] The low temperature difference means that water volumes must be very large to extract useful amounts of heat. A 100MW power plant would be expected to pump on the order of 12 million gallons (44,400 tonnes) per minute.[95] For comparison, pumps must move a mass of water greater than the weight of the battleship Bismarck, which weighed 41,700 tonnes, every minute. This makes pumping a substantial parasitic drain on energy production in OTEC systems, with one Lockheed design consuming 19.55 MW in pumping costs for every 49.8 MW net electricity generated. For OTEC schemes using heat exchangers, to handle this volume of water the exchangers need to be enormous compared to those used in conventional thermal power generation plants,[96] making them one of the most critical components due to their impact on overall efficiency. A 100 MW OTEC power plant would require 200 exchangers each larger than a 20-foot shipping container making them the single most expensive component.[97]

### Variation of ocean temperature with depth

Graph of different thermoclines (depth vs. temperature) based on seasons and latitude

The total insolation received by the oceans (covering 70% of the earth's surface, with clearness index of 0.5 and average energy retention of 15%) is: 5.45×1018 MJ/yr × 0.7 × 0.5 × 0.15 = 2.87×1017 MJ/yr

We can use Beer–Lambert–Bouguer's law to quantify the solar energy absorption by water,

${\displaystyle -{\frac {dI(y)}{dy))=\mu I}$

where, y is the depth of water, I is intensity and μ is the absorption coefficient. Solving the above differential equation,

${\displaystyle I(y)=I_{0}\exp(-\mu y)\,}$

The absorption coefficient μ may range from 0.05 m−1 for very clear fresh water to 0.5 m−1 for very salty water.

Since the intensity falls exponentially with depth y, heat absorption is concentrated at the top layers. Typically in the tropics, surface temperature values are in excess of 25 °C (77 °F), while at 1 kilometer (0.62 mi), the temperature is about 5–10 °C (41–50 °F). The warmer (and hence lighter) waters at the surface means there are no thermal convection currents. Due to the small temperature gradients, heat transfer by conduction is too low to equalize the temperatures. The ocean is thus both a practically infinite heat source and a practically infinite heat sink.[clarification needed]

This temperature difference varies with latitude and season, with the maximum in tropical, subtropical and equatorial waters. Hence the tropics are generally the best OTEC locations.

### Open/Claude cycle

In this scheme, warm surface water at around 27 °C (81 °F) enters an evaporator at pressure slightly below the saturation pressures causing it to vaporize.

${\displaystyle H_{1}=H_{f}\,}$

Where Hf is enthalpy of liquid water at the inlet temperature, T1.

This temporarily superheated water undergoes volume boiling as opposed to pool boiling in conventional boilers where the heating surface is in contact. Thus the water partially flashes to steam with two-phase equilibrium prevailing. Suppose that the pressure inside the evaporator is maintained at the saturation pressure, T2.

${\displaystyle H_{2}=H_{1}=H_{f}+x_{2}H_{fg}\,}$

Here, x2 is the fraction of water by mass that vaporizes. The warm water mass flow rate per unit turbine mass flow rate is 1/x2.

The low pressure in the evaporator is maintained by a vacuum pump that also removes the dissolved non-condensable gases from the evaporator. The evaporator now contains a mixture of water and steam of very low vapor quality (steam content). The steam is separated from the water as saturated vapor. The remaining water is saturated and is discharged to the ocean in the open cycle. The steam is a low pressure/high specific volume working fluid. It expands in a special low pressure turbine.

${\displaystyle H_{3}=H_{g}\,}$

Here, Hg corresponds to T2. For an ideal isentropic (reversible adiabatic) turbine,

${\displaystyle s_{5,s}=s_{3}=s_{f}+x_{5,s}s_{fg}\,}$

The above equation corresponds to the temperature at the exhaust of the turbine, T5. x5,s is the mass fraction of vapor at state 5.

The enthalpy at T5 is,

${\displaystyle H_{5,s}=H_{f}+x_{5,s}H_{fg}\,}$

This enthalpy is lower. The adiabatic reversible turbine work = H3-H5,s .

Actual turbine work WT = (H3-H5,s) x polytropic efficiency

${\displaystyle H_{5}=H_{3}-\ \mathrm {actual} \ \mathrm {work} }$

The condenser temperature and pressure are lower. Since the turbine exhaust is to be discharged back into the ocean, a direct contact condenser is used to mix the exhaust with cold water, which results in a near-saturated water. That water is now discharged back to the ocean.

H6=Hf, at T5. T7 is the temperature of the exhaust mixed with cold sea water, as the vapor content now is negligible,

${\displaystyle H_{7}\approx H_{f}\,\ at\ T_{7}\,}$

The temperature differences between stages include that between warm surface water and working steam, that between exhaust steam and cooling water, and that between cooling water reaching the condenser and deep water. These represent external irreversibilities that reduce the overall temperature difference.

The cold water flow rate per unit turbine mass flow rate,

${\displaystyle {\dot {m_{c}={\frac {H_{5}-\ H_{6)){H_{6}-\ H_{7))))}\,}$

Turbine mass flow rate, ${\displaystyle {\dot {M_{T))}={\frac {\mathrm {turbine} \ \mathrm {work} \ \mathrm {required} }{W_{T))))$

Warm water mass flow rate, ${\displaystyle {\dot {M_{w))}={\dot {M_{T}{\dot {m_{w))))}\,}$

Cold water mass flow rate ${\displaystyle {\dot ((\dot {M_{c))}={\dot {M_{T}m_{C))))}\,}$

### Closed Anderson cycle

As developed starting in the 1960s by J. Hilbert Anderson of Sea Solar Power, Inc., in this cycle, QH is the heat transferred in the evaporator from the warm sea water to the working fluid. The working fluid exits the evaporator as a gas near its dew point.

The high-pressure, high-temperature gas then is expanded in the turbine to yield turbine work, WT. The working fluid is slightly superheated at the turbine exit and the turbine typically has an efficiency of 90% based on reversible, adiabatic expansion.

From the turbine exit, the working fluid enters the condenser where it rejects heat, -QC, to the cold sea water. The condensate is then compressed to the highest pressure in the cycle, requiring condensate pump work, WC. Thus, the Anderson closed cycle is a Rankine-type cycle similar to the conventional power plant steam cycle except that in the Anderson cycle the working fluid is never superheated more than a few degrees Fahrenheit. Owing to viscosity effects, working fluid pressure drops in both the evaporator and the condenser. This pressure drop, which depends on the types of heat exchangers used, must be considered in final design calculations but is ignored here to simplify the analysis. Thus, the parasitic condensate pump work, WC, computed here will be lower than if the heat exchanger pressure drop was included. The major additional parasitic energy requirements in the OTEC plant are the cold water pump work, WCT, and the warm water pump work, WHT. Denoting all other parasitic energy requirements by WA, the net work from the OTEC plant, WNP is

${\displaystyle W_{NP}=W_{T}-W_{C}-W_{CT}-W_{HT}-W_{A}\,}$

The thermodynamic cycle undergone by the working fluid can be analyzed without detailed consideration of the parasitic energy requirements. From the first law of thermodynamics, the energy balance for the working fluid as the system is

${\displaystyle W_{N}=Q_{H}-Q_{C}\,}$

where WN = WT + WC is the net work for the thermodynamic cycle. For the idealized case in which there is no working fluid pressure drop in the heat exchangers,

${\displaystyle Q_{H}=\int _{H}T_{H}ds\,}$

and

${\displaystyle Q_{C}=\int _{C}T_{C}ds\,}$

so that the net thermodynamic cycle work becomes

${\displaystyle W_{N}=\int _{H}T_{H}ds-\int _{C}T_{C}ds\,}$

Subcooled liquid enters the evaporator. Due to the heat exchange with warm sea water, evaporation takes place and usually superheated vapor leaves the evaporator. This vapor drives the turbine and the 2-phase mixture enters the condenser. Usually, the subcooled liquid leaves the condenser and finally, this liquid is pumped to the evaporator completing a cycle.

## Environmental impact

Carbon dioxide dissolved in deep cold and high pressure layers is brought up to the surface and released as the water warms.[citation needed]

Mixing of deep ocean water with shallower water brings up nutrients and makes them available to shallow water life. This may be an advantage for aquaculture of commercially important species, but may also unbalance the ecological system around the power plant.[citation needed]

OTEC plants use very large flows of warm surface seawater and cold deep seawater to generate constant renewable power. The deep seawater is oxygen deficient and generally 20-40 times more nutrient rich (in nitrate and nitrite) than shallow seawater. When these plumes are mixed, they are slightly denser than the ambient seawater.[98] Though no large scale physical environmental testing of OTEC has been done, computer models have been developed to simulate the effect of OTEC plants.

### Hydrodynamic modeling

In 2010, a computer model was developed to simulate the physical oceanographic effects of one or several 100 megawatt OTEC plant(s). The model suggests that OTEC plants can be configured such that the plant can conduct continuous operations, with resulting temperature and nutrient variations that are within naturally occurring levels. Studies to date suggest that by discharging the OTEC flows downwards at a depth below 70 meters, the dilution is adequate and nutrient enrichment is small enough so that 100-megawatt OTEC plants could be operated in a sustainable manner on a continuous basis.[99]

### Biological modeling

The nutrients from an OTEC discharge could potentially cause increased biological activity if they accumulate in large quantities in the photic zone.[99] In 2011 a biological component was added to the hydrodynamic computer model to simulate the biological response to plumes from 100 megawatt OTEC plants. In all cases modeled (discharge at 70 meters depth or more), no unnatural variations occurs in the upper 40 meters of the ocean's surface.[98] The picoplankton response in the 110 - 70 meter depth layer is approximately a 10-25% increase, which is well within naturally occurring variability. The nanoplankton response is negligible. The enhanced productivity of diatoms (microplankton) is small. The subtle phytoplankton increase of the baseline OTEC plant suggests that higher-order biochemical effects will be very small.[98]

### Studies

A previous Final Environmental Impact Statement (EIS) for the United States' NOAA from 1981 is available,[100] but needs to be brought up to current oceanographic and engineering standards. Studies have been done to propose the best environmental baseline monitoring practices, focusing on a set of ten chemical oceanographic parameters relevant to OTEC.[101] Most recently, NOAA held an OTEC Workshop in 2010 and 2012 seeking to assess the physical, chemical, and biological impacts and risks, and identify information gaps or needs.[102][103]

The Tethys database provides access to scientific literature and general information on the potential environmental effects of OTEC.[104]

## Technical difficulties

### Dissolved gases

The performance of direct contact heat exchangers operating at typical OTEC boundary conditions is important to the Claude cycle. Many early Claude cycle designs used a surface condenser since their performance was well understood. However, direct contact condensers offer significant disadvantages. As cold water rises in the intake pipe, the pressure decreases to the point where gas begins to evolve. If a significant amount of gas comes out of solution, placing a gas trap before the direct contact heat exchangers may be justified. Experiments simulating conditions in the warm water intake pipe indicated about 30% of the dissolved gas evolves in the top 8.5 meters (28 ft) of the tube. The trade-off between pre-dearation[105] of the seawater and expulsion of non-condensable gases from the condenser is dependent on the gas evolution dynamics, deaerator efficiency, head loss, vent compressor efficiency and parasitic power. Experimental results indicate vertical spout condensers perform some 30% better than falling jet types.

### Microbial fouling

Because raw seawater must pass through the heat exchanger, care must be taken to maintain good thermal conductivity. Biofouling layers as thin as 25 to 50 micrometres (0.00098 to 0.00197 in) can degrade heat exchanger performance by as much as 50%.[41] A 1977 study in which mock heat exchangers were exposed to seawater for ten weeks concluded that although the level of microbial fouling was low, the thermal conductivity of the system was significantly impaired.[106] The apparent discrepancy between the level of fouling and the heat transfer impairment is the result of a thin layer of water trapped by the microbial growth on the surface of the heat exchanger.[106]

Another study concluded that fouling degrades performance over time, and determined that although regular brushing was able to remove most of the microbial layer, over time a tougher layer formed that could not be removed through simple brushing.[41] The study passed sponge rubber balls through the system. It concluded that although the ball treatment decreased the fouling rate it was not enough to completely halt growth and brushing was occasionally necessary to restore capacity. The microbes regrew more quickly later in the experiment (i.e. brushing became necessary more often) replicating the results of a previous study.[107] The increased growth rate after subsequent cleanings appears to result from selection pressure on the microbial colony.[107]

Continuous use of 1 hour per day and intermittent periods of free fouling and then chlorination periods (again 1 hour per day) were studied. Chlorination slowed but did not stop microbial growth; however chlorination levels of .1 mg per liter for 1 hour per day may prove effective for long term operation of a plant.[41] The study concluded that although microbial fouling was an issue for the warm surface water heat exchanger, the cold water heat exchanger suffered little or no biofouling and only minimal inorganic fouling.[41]

Besides water temperature, microbial fouling also depends on nutrient levels, with growth occurring faster in nutrient rich water.[108] The fouling rate also depends on the material used to construct the heat exchanger. Aluminium tubing slows the growth of microbial life, although the oxide layer which forms on the inside of the pipes complicates cleaning and leads to larger efficiency losses.[107] In contrast, titanium tubing allows biofouling to occur faster but cleaning is more effective than with aluminium.[107]

### Sealing

The evaporator, turbine, and condenser operate in partial vacuum ranging from 3% to 1% of atmospheric pressure. The system must be carefully sealed to prevent in-leakage of atmospheric air that can degrade or shut down operation. In closed-cycle OTEC, the specific volume of low-pressure steam is very large compared to that of the pressurized working fluid. Components must have large flow areas to ensure steam velocities do not attain excessively high values.

### Parasitic power consumption by exhaust compressor

An approach for reducing the exhaust compressor parasitic power loss is as follows. After most of the steam has been condensed by spout condensers, the non-condensible gas steam mixture is passed through a counter current region which increases the gas-steam reaction by a factor of five. The result is an 80% reduction in the exhaust pumping power requirements.

## Cold air/warm water conversion

 Further information: Lake Vanda

In winter in coastal Arctic locations, the temperature difference between the seawater and ambient air can be as high as 40 °C (72 °F). Closed-cycle systems could exploit the air-water temperature difference. Eliminating seawater extraction pipes might make a system based on this concept less expensive than OTEC. This technology is due to H. Barjot, who suggested butane as cryogen, because of its boiling point of −0.5 °C (31.1 °F) and its non-solubility in water.[109] Assuming a realistic level of efficiency of 4%, calculations show that the amount of energy generated with one cubic meter water at a temperature of 2 °C (36 °F) in a place with an air temperature of −22 °C (−8 °F) equals the amount of energy generated by letting this cubic meter water run through a hydroelectric plant of 4000 feet (1,200 m) height.[110]

Barjot Polar Power Plants could be located on islands in the polar region or designed as swimming barges or platforms attached to the ice cap. The weather station Myggbuka at Greenlands east coast for example, which is only 2,100 km away from Glasgow, detects monthly mean temperatures below −15 °C (5 °F) during 6 winter months in the year.[111] This technology can also be used to create artificial ice caps or glaciers on Antarctica valleys located near the sea coast. Thus sea level rise due to carbon emissions can be mitigated and also the generated electricity is used for Bitcoin currency mining and the heat liberated in the process is utilized for space heating requirements.

In this article "Proposal_of_an_aeraulic_thermosiphon", it is envisaged different possibilities to generate electric energy from the difference of temperatures between the ambient atmospheric air and the surface sea water. Finally, it is proposed a machine based on an aeraulic thermosiphon, installed between the seashore and a high relief (300 m at least). This electric generation would be done without insoluble constraints on the refrigerant, but, unfortunately, at high cost.

## Application of the thermoelectric effect

In 1979 SERI proposed using the Seebeck effect to produce power with a total conversion efficiency of 2%.[112]

In 2014 Liping Liu, Associate Professor at Rutgers University, envisioned an OTEC system that utilises the solid state thermoelectric effect rather than the fluid cycles traditionally used.[113][114]

## References

1. ^ Lewis, Anthony, et al. IPCC: Special Report on Renewable Energy Sources and Climate Change Mitigation, 2011
2. ^ World Energy Council, 2000
3. ^ Pelc and Fujita, 2002
4. ^ a b c DiChristina, Mariette (May 1995). "Sea Power". Popular Science: 70–73. Retrieved 2016-10-09.
5. ^
6. ^ Chiles, Jamesin (Winter 2009). "The Other Renewable Energy". Invention and Technology. 23 (4): 24–35.
7. ^ "Power from the Sea" Popular Mechanics, December 1930, pp 881-882 detail article and photos of Cuban power plant
8. ^ a b c d Takahashi, Masayuki Mac (2000) [1991]. Deep Ocean Water as Our Next Natural Resource. Translated by Kitazawa, Kazuhiro; Snowden, Paul. Tokyo, Japan: Terra Scientific Publishing Company. ISBN 978-4-88704-125-7.
9. ^ a b Avery, William H. and Chih Wu. Renewable Energy From the Ocean: A Guide to OTEC. New York: Oxford University Press. 1994.
10. ^ US patent 3312054, J.H. Anderson, "Sea Water Power Plant", issued 1967-04-04
11. ^ a b Bruch, Vicki L. (April 1994). An Assessment of Research and Development Leadership in Ocean Energy Technologies (Report). Albuquerque, NM: Sandia National Laboratories: Energy Policy and Planning Department. doi:10.2172/10154003. SAND93-3946.
12. ^ Mitsui T, Ito F, Seya Y, Nakamoto Y (September 1983). "Outline of the 100 kW OTEC Pilot Plant in the Republic of Nauru". IEEE Transactions on Power Apparatus and Systems. PAS-102 (9): 3167–3171. Bibcode:1983ITPAS.102.3167M. doi:10.1109/TPAS.1983.318124. S2CID 8924555. Archived from the original on 2008-05-02.
13. ^ Finney, Karen Anne. "Ocean Thermal Energy Conversion". Guelph Engineering Journal. 2008.
14. ^ Daly, John (December 5, 2011). "Hawaii About to Crack Ocean Thermal Energy Conversion Roadblocks?". OilPrice.com. Retrieved 28 March 2013.
15. ^
16. ^ a b L. Meyer; D. Cooper; R. Varley. "Are We There Yet? A Developer's Roadmap to OTEC Commercialization" (PDF). Hawaii National Marine Renewable Energy Center. Retrieved 28 March 2013.
17. ^ "Curaçao". Retrieved 28 April 2020.
18. ^ Bharathan, D.; Penney, T. R. (1984). Flash Evaporation from Turbulent Water Jets. Journal of Heat Transfer. Vol. 106(2), May 1984; pp. 407-416.
19. ^ Bharathan, D. (1984). Method and Apparatus for Flash Evaporation of Liquids. U.S. Patent No. 4,474,142.
20. ^ Bharathan, D.; Parsons, B. K.; Althof, J. A. (1988). Direct-Contact Condensers for Open-Cycle OTEC Applications: Model Validation with Fresh Water Experiments for Structured Packings. 272 pp.; NREL Report No. TR-253-3108.
21. ^ Bharathan, D.; Kreith, F.; Schlepp, D. R.; Owens, W. L. (1984). Heat and Mass Transfer in Open-Cycle OTEC Systems. Heat Transfer Engineering. Vol. 5(1-2); pp. 17-30.
22. ^ Kreith, F.; Bharathan, D. (1988). Heat Transfer Research for Ocean Thermal Energy Conversion. Journal of Heat Transfer. Vol. 110, February 1988; pp. 5-22.
23. ^ Bharathan, D.; Green, H. J.; Link, H. F.; Parsons, B. K.; Parsons, J. M.; Zangrando, F. (1990). Conceptual Design of an Open-Cycle Ocean Thermal Energy Conversion Net Power-Producing Experiment (OC-OTEC NPPE). 160 pp.; NREL Report No. TR-253-3616.
24. ^ Avery, William H. and Chih Wu. Renewable Energy From the Ocean: A Guide to OTEC. New York: Oxford University Press. 1994.
25. ^ "Deep Pipelines for Ocean Thermal Energy Conversion". Retrieved 8 January 2020.
26. ^ Spaine (19 December 2011). "Baha Mar Resort Signs Energy Services Agreement with OTE Corporation".
27. ^ Carlyle, Erin. "Baha Mar Resorts To Chapter 11 Bankruptcy, Blames China Construction For Delays". Forbes.
28. ^ a b "Archived copy". Archived from the original on 2016-10-14. Retrieved 2016-10-13.((cite web)): CS1 maint: archived copy as title (link)
29. ^ "Makai Ocean Engineering's Heat Exchanger Test Facility opened". www.otecnews.org. 2011-11-22. Retrieved 28 March 2013.
30. ^ "Makai Ocean Engineering working with Navy on Big Island OTEC project". Retrieved 28 March 2013.
31. ^ "Makai Ocean Engineering to add 100kW turbine generator to Kona, Hawaii OTEC test facility". International District Energy Association. Archived from the original on 2014-11-10. Retrieved 2013-03-28.
32. ^ a b "OTE Receives Approval for OTEC System in the USVI". 18 July 2016.
33. ^ a b Mekeel, Tim. "Ocean Thermal to begin talks for renewable energy plants in St. Croix, St. Thomas". LancasterOnline.
34. ^ "OTEC Okinawa Project". otecokinawa.com.
35. ^ "Contact". otecokinawa.com.
36. ^
37. ^
38. ^ Celebrating Hawaii ocean thermal energy conversion power plant Physorg 25 August 2015
39. ^ Kempener, Ruud (June 2014). "Wave Energy Technological Brief" (PDF): 3. Retrieved 2020-04-28. ((cite journal)): Cite journal requires |journal= (help)
40. ^ "What Is OTEC?". 2016. Retrieved 2020-04-28. ((cite journal)): Cite journal requires |journal= (help)
41. Berger LR, Berger JA (June 1986). "Countermeasures to Microbiofouling in Simulated Ocean Thermal Energy Conversion Heat Exchangers with Surface and Deep Ocean Waters in Hawaii". Appl. Environ. Microbiol. 51 (6): 1186–1198. Bibcode:1986ApEnM..51.1186B. doi:10.1128/AEM.51.6.1186-1198.1986. PMC 239043. PMID 16347076.
42. ^ US patent 4311012, Warren T. Finley, "Method and apparatus for transferring cold seawater upward from the lower depths of the ocean to improve the efficiency of ocean thermal energy conversion systems", issued 1982-01-19
43. ^ Shah, Yatish T. (2018-01-12). Thermal Energy: Sources, Recovery, and Applications. CRC Press. ISBN 9781315305936.
44. ^ Trimble LC, Owens WL (1980). "Review of mini-OTEC performance". Energy to the 21st Century; Proceedings of the Fifteenth Intersociety Energy Conversion Engineering Conference. 2: 1331–1338. Bibcode:1980iece.conf.1331T.
45. ^ Vega, L.A. (1999). "Open Cycle OTEC". OTEC News. The GreenOcean Project. Archived from the original on 7 December 2008. Retrieved 4 February 2011.
46. ^ Lee, C.K.B.; Ridgway, Stuart (May 1983). "Vapor/Droplet Coupling and the Mist Flow (OTEC) Cycle" (PDF). Journal of Solar Energy Engineering. 105 (2): 181. Bibcode:1983ATJSE.105..181L. doi:10.1115/1.3266363.
47. ^ a b
48. ^ Vega, L. A. (2002-12-01). "Ocean Thermal Energy Conversion Primer". Marine Technology Society Journal. 36 (4): 25–35. doi:10.4031/002533202787908626.
49. ^ a b c d "Design and Location". What is Ocean Thermal Energy Conversion?. National Renewable Energy Laboratory. Retrieved 22 January 2012.
50. ^ Shah, Yatish (2018-01-31). Thermal Energy: Sources, Recovery, and Applications. CRC Press. ISBN 9781138033535.
51. ^ Vega, Luis A. (May 2010). "Economics of Ocean Thermal Energy Conversion" (PDF). National Marine Renewable Energy Center at the University of Hawaii. p. 11. Retrieved 13 December 2019.
52. ^ "Levelized cost of energy for ocean energy technologies". Ocean Energy Systems. May 2015. p. 41. Retrieved 13 December 2019.
53. ^ www.pichtr.org (PDF) https://web.archive.org/web/20070626183941/http://www.pichtr.org/luis_vega_otec_summary.pdf. Archived from the original (PDF) on June 26, 2007. ((cite web)): Missing or empty |title= (help)
54. ^ "Lazard's Levelized Cost of Energy" (PDF). p. 3. Retrieved November 29, 2019.
55. ^ (PDF) https://www.irena.org/documentdownloads/publications/ocean_thermal_energy_v4_web.pdf. Retrieved April 28, 2019. ((cite web)): Missing or empty |title= (help)
56. ^ "NREL: Ocean Thermal Energy Conversion - Markets for OTEC". Nrel.gov. Archived from the original on 2005-11-26. Retrieved 2012-06-12.
57. ^ "NREL: Ocean Thermal Energy Conversion Home Page". Nrel.gov. Retrieved 2012-06-12.
58. ^
59. ^ Carlyle, Erin. "Baha Mar Resorts To Chapter 11 Bankruptcy, Blames China Construction For Delays". Forbes.
60. ^ Guardian, The Nassau (8 August 2012). "News Article".
61. ^
62. ^ "Lockheed Martin awarded another \$4.4M for OTEC work in Hawaii". November 22, 2010. Retrieved 6 December 2010.
63. ^ Coxworth, Ben (November 26, 2010). "More funds for Hawaii's Ocean Thermal Energy Conversion plant". Retrieved 6 December 2010.
64. ^ Hawaii First to Harness Deep Ocean Temperatures for Power http://www.scientificamerican.com/article/hawaii-first-to-harness-deep-ocean-temperatures-for-power/
65. ^ Daniel Cusick (May 1, 2013). "CLEAN TECHNOLOGY: U.S.-designed no-emission power plant will debut off China's coast". ClimateWire E&E Publishing. Retrieved May 2, 2013.
66. ^ David Alexander (April 16, 2013). "Lockheed to build 10-megawatt thermal power plant off southern China". Reuters. Retrieved April 17, 2013.
67. ^ "Tapping Into the Ocean's Power: Lockheed Martin signs agreement for largest ever OTEC plant". Lockheed Martin. Retrieved April 17, 2013.
68. ^ "Reignwood Ocean Engineering". Reignwood Group. Archived from the original on January 15, 2013. Retrieved April 17, 2013.
69. ^ Martin, Benjamin (4 August 2014). "The Foundation of GO SEA".
70. ^ "OTEC：Ocean Thermal Energy Conversion - Xenesys Inc". xenesys.com.
71. ^ "Home". otecorporation.com.
72. ^ "Senate Signs MOU for Ocean Energy Feasibility Study". 6 March 2014.
73. ^
74. ^ "Energy from the Ocean: The Ocean Thermal Energy Converter". Marine Technology News. 29 January 2016.
75. ^
77. ^ otecfoundation (9 July 2014). "Funding NEMO: Offshore OTEC project awarded in NER 300 program". OTEC news.
78. ^ a b "OTECresorts: Ocean Energy at East Anglia, United Kingdom". www.angelinvestmentnetwork.co.uk. Angel Investment Network. Retrieved 2018-02-21.
79. ^ "Applications open for ocean thermal energy purchase in Maldives". Retrieved 8 January 2020.
80. ^ "UK OTEC developer kicks off crowdfunding campaign". Tidal Energy Today. Retrieved 2018-02-21.
81. ^ Block and Lalenzuela 1985
82. ^
83. ^ "海洋エネルギー研究センター 2015久米島サテライトオープンラボ (施設見学会)[報告]". Retrieved 2015-06-16.
84. ^ Martin, Benjamin. "IOES Kumejima Satellite". otecokinawa.com. Archived from the original on 2020-06-07. Retrieved 2015-06-16.
85. ^
86. ^ "YouTube video on the OTEC air-conditioning system used at the InterContinental Resort and Thalasso-Spa on the island of Bora Bora". YouTube. Archived from the original on 2011-11-04. Retrieved 2007-05-28.
87. ^ Green Tech. "Copenhagen’s SeawaterCooling Delivers Energy And Carbon Savings". 24 October 2012. Forbes.
88. ^
89. ^ "Deep Sea Water Research Institute". kumeguide.com. 16 August 2019.
90. ^ Ponia, Ben. "Aquaculture Updates in the Northern Pacific: Hawaii, Federated States of Mirconesia, Palau and Saipan". SPCFisheries Newsletter. July 2006. Web. 25 June 2013. available at: http://www.spc.int/DigitalLibrary/Doc/FAME/InfoBull/FishNews/118/FishNews11 Archived 2015-09-25 at the Wayback Machine 8_58_Ponia.pdf.
91. ^ Shah, Yatish (2014-05-16). Water for Energy and Fuel Production. CRC Press. ISBN 978-1482216189.
92. ^ Wu, Chih (1994). Renewable Energy From The Ocean. Oxford University Press. ISBN 9780195071993.
93. ^ Berger, Matthew. "The Nuclear Option: Technology to Extract Uranium From the Sea Advances". NewsDeeply.
94. ^ "Enhancing fish stocks with artificial upwelling". CiteSeerX 10.1.1.526.2024. ((cite journal)): Cite journal requires |journal= (help)
95. ^ Hartman, Duke (October 2011), "Challenge And Promise Of OTEC", Ocean News, retrieved 11 June 2012
96. ^ Da Rosa, Aldo Vieira (2009). "Chapter 4:Ocean Thermal Energy Converters". Fundamentals of renewable energy processes. Academic Press. pp. 139 to 152. ISBN 978-0-12-374639-9.
97. ^ Eldred, M.; Landherr, A.; Chen, I.C. (July 2010), "Comparison Of Aluminum Alloys And Manufacturing Processes Based On Corrosion Performance For Use In OTEC Heat Exchangers", Offshore Technology Conference 2010 (OTC 2010), Curran Associates, Inc., doi:10.4043/20702-MS, ISBN 9781617384264
98. ^ a b c Grandelli, Pat (2012). "Modeling the Physical and Biochemical Influence of Ocean Thermal Energy Conversion Plant Discharges into their Adjacent Waters" (PDF). US Department of Energy - Office of Scientific and Technical Information. doi:10.2172/1055480. Retrieved 27 March 2013.
99. ^ a b Rocheleau, Greg J.; Grandelli, Patrick (2011). "Physical and biological modeling of a 100 megawatt Ocean Thermal Energy Conversion discharge plume". Oceans'11 MTS/IEEE Kona. pp. 1–10. doi:10.23919/OCEANS.2011.6107077. ISBN 978-1-4577-1427-6. S2CID 22549789.
100. ^ "Final Environmental Impact Statement for Commercial Ocean Thermal Energy Conversion (OTEC) Licensing" (PDF). U.S. Dept of Commerce, National Oceanic and Atmospheric Administration. Retrieved 27 March 2013.
101. ^ L. Vega; C. Comfort. "Environmental Assessment of Ocean Thermal Energy Conversion in Hawaii" (PDF). Hawaii National Marine Renewable Energy Center. Retrieved 27 March 2013.
102. ^ "Ocean Thermal Energy Conversion: Assessing Potential Physical, Chemical, and Biological Impacts and Risks" (PDF). National Oceanic and Atmospheric Administration, Office of Ocean and Coastal Resource Management. Retrieved 27 March 2013.
103. ^ "Ocean Thermal Energy Conversion: Information Needs Assessment" (PDF). National Oceanic and Atmospheric Administration (NOAA) Office of Response and Restoration (ORR) and the Environmental Research Group at the University of New Hampshire (UNH). Retrieved 27 March 2013.
104. ^ "Tethys". Archived from the original on 2014-11-10.
105. ^ "Definition of DEAERATE". www.merriam-webster.com.
106. ^ a b Aftring RP, Taylor BF (October 1979). "Assessment of Microbial Fouling in an Ocean Thermal Energy Conversion Experiment". Appl. Environ. Microbiol. 38 (4): 734–739. Bibcode:1979ApEnM..38..734A. doi:10.1128/AEM.38.4.734-739.1979. PMC 243568. PMID 16345450.
107. ^ a b c d Nickels JS, Bobbie RJ, Lott DF, Martz RF, Benson PH, White DC (June 1981). "Effect of Manual Brush Cleaning on Biomass and Community Structure of Microfouling Film Formed on Aluminum and Titanium Surfaces Exposed to Rapidly Flowing Seawater". Appl. Environ. Microbiol. 41 (6): 1442–1453. Bibcode:1981ApEnM..41.1442N. doi:10.1128/AEM.41.6.1442-1453.1981. PMC 243937. PMID 16345798.
108. ^ Trulear MG, Characklis, WG (September 1982). "Dynamics of Biofilm Processes". Journal of the Water Pollution Control Federation. 54 (9): 1288–1301. Archived from the original on 2008-05-02. Retrieved 2008-01-27.
109. ^ "Science: Cold Power". Time. 1929-04-22.
110. ^ "Achmed Khammas - Das Buch der Synergie - Teil C - Temperaturgradient". Buch-der-synergie.de. 2007-10-25. Retrieved 2012-06-12.
111. ^ "Denmark - Myggbuka". Globalbioclimatics.org. Retrieved 2012-06-12.
112. ^ "Archived copy" (PDF). Archived from the original (PDF) on 2018-10-11. Retrieved 2018-10-10.((cite web)): CS1 maint: archived copy as title (link)
113. ^ Thermoelectric power plants could offer economically competitive renewable energy PhysOrg.com, Dec 19, 2014.
114. ^ Liu, Liping (2014). "Feasibility of large-scale power plants based on thermoelectric effects". New Journal of Physics. 16 (12): 123019. Bibcode:2014NJPh...16l3019L. doi:10.1088/1367-2630/16/12/123019.