Architectural lighting design is a field of work or study that is concerned with the design of lighting systems within the built environment, both interior and exterior. It can include manipulation and design of both daylight and electric light or both, to serve human needs.
Lighting design is based in both science and the visual arts. The basic aim of lighting within the built environment is to enable occupants to see clearly and without discomfort. The objective of architectural lighting design is to balance the art and the science of lighting to create mood, visual interest and enhance the experience of a space or place whilst still meeting the technical and safety requirements.
The purpose of architectural lighting design is to balance the characteristics of light within a space to optimize the technical, the visual and, most recently, the non-visual components of ergonomics with respect to illumination of buildings or spaces.
The technical requirements include the amount of light needed to perform a task, the energy consumed by the lighting within the space and the relative distribution and direction of travel for the light so as not to cause unnecessary glare and discomfort. The visual aspects of the light are those that are concerned with the aesthetics and the narrative of the space (e.g. the mood of a restaurant, the experience of an exhibition within a museum, the promotion of goods within a retail space, the reinforcement of corporate brand) and the non-visual aspects are those concerned with human health and well-being.
As part of the lighting design process both cultural and contextual factors also need to be considered. For example, bright lighting was a mark of wealth through much of Chinese history, but if uncontrolled bright lights are known to be detrimental the effect of insects, bird and the view of stars.
The history of electric light is well documented, and with the developments in lighting technology the profession of lighting developed alongside it. The development of high-efficiency, low-cost fluorescent lamps led to a reliance on electric light and a uniform blanket approach to lighting, but the energy crisis of the 1970s required more design consideration and reinvigorated the use of daylight.
The Illuminating Engineering Society of North America (IESNA) was formed in 1906 and UK version was established in 1909 (now known as the Society of Light and Lighting and part of CIBSE). The International Commission on Illumination (CIE) was established in 1913 and has become a professional organization accepted as representing the best authority on the subject matter of light and lighting. The Institution of Lighting Professionals was established as the Association of Public Lighting Engineers in 1924. Around the world similar professional organizations evolved.
Initially, these industry organizations were primarily focused on the science and engineering of lighting rather than the aesthetic design, but in 1969 a group of designers established the International Association of Lighting Designers (IALD). Other associations purely for lighting design include the Professional Lighting Designers' Association (PLDA) established in 1994, the Association de Concepteurs Eclairage (ACE) in France established 1995, the Associazione Professionisti dell'Illuminazione (APIL) in Italy established in 1998, the Associação Brasileira de Arquitetos de Iluminação in Brazil in 1999 and the Professional Association of Lighting Designers in Spain (APDI) established in 2008.
See also: Lighting designer
Architectural lighting designer is a stand-alone profession that sits alongside the professions of architecture, interior design, landscape architecture and electrical engineering.
One of the earliest proponents of architectural lighting design was Richard Kelly who established his practice in 1935. Kelly developed an approach to architectural lighting that is still used today, based on the perception of three visual elements as presented in a 1952 joint meeting of The American Institute of Architects, the American Society of Industrial Designers (now the Industrial Designers Society of America), and the Illuminating Engineering Society of North America, in Cleveland.
While many architectural lighting designers have a background in electrical engineering, architectural engineering, architecture, or luminaire manufacturing, several universities and technical schools now offer degree programs specifically in architectural lighting design.
The process of architectural lighting design generally follows the architect's plan of works in terms of key project stages: feasibility, concept, detail, construction documentation, site supervision and commissioning.
After the feasibility stage, where the parameters for the project are set, the concept stage is when the lighting design is developed in terms of lit effect, technical lighting targets and overall visual strategy usually using concept sketches, renderings, or mood boards.
For colors based on black-body theory, blue occurs at higher temperatures, while red occurs at lower, cooler, temperatures. This is the opposite of the cultural associations attributed to colors, in which red represents hot, and blue cold.
Main article: Light fixture
Lighting fixtures come in a wide variety of styles for various functions. The most important functions are as a holder for the light source, to provide directed light and to avoid visual glare. Some are very plain and functional, while some are pieces of art in themselves. Nearly any material can be used, so long as it can tolerate the excess heat and is in keeping with safety codes.
An important property of light fixtures is the luminous efficacy or wall-plug efficiency, meaning the amount of usable light emanating from the fixture per used energy, usually measured in lumen per watt. A fixture using replaceable light sources can also have its efficiency quoted as the percentage of light passed from the "bulb" to the surroundings. The more transparent the lighting fixture is, the higher efficacy. Shading the light will normally decrease efficiency but increase the directionality and the visual comfort probability.
The PH-lamps are a series of light fixtures designed by Danish designer and writer Poul Henningsen from 1926 onwards. The lamp is designed with multiple concentric shades to eliminate visual glare, only emitting reflected light, obscuring the light source.
Photometric studies are performed to simulate lighting designs for projects before they are built or renovated. This enables architects, lighting designers, and engineers to determine whether a proposed lighting layout will deliver the amount of light intended. They will also be able to determine the contrast ratio between light and dark areas. In many cases these studies are referenced against IESNA or CIBSE recommended lighting practices for the type of application. Depending on the type of area, different design aspects may be emphasized for safety or practicality (i.e. such as maintaining uniform light levels, avoiding glare or highlighting certain areas). A specialized lighting design application is often used to create these, which typically combine the use of two-dimensional digital CAD drawings and lighting simulation software.
Color temperature for white light sources also affects their use for certain applications. The color temperature of a white light source is the temperature in kelvin of a theoretical black body emitter that most closely matches the spectral characteristics of the lamp. Incandescent light bulbs have a color temperature around 2700 to 3000 kelvin; daylight is around 6400 kelvin. Lower color temperature lamps have relatively more energy in the yellow and red part of the visible spectrum, while high color temperatures correspond to lamps with more of a blue-white appearance. For critical inspection or color matching tasks, or for retail displays of food and clothing, the color temperature of the lamps will be selected for the best overall lighting effect. Color may also be used for functional reasons. For example, blue light makes it difficult to see veins and thus may be used to discourage drug use.
For simple installations, hand-calculations based on tabular data can be used to provide an acceptable lighting design. More critical or optimized designs now routinely use mathematical modeling on a computer.
Based on the positions and mounting heights of the fixtures, and their photometric characteristics, the proposed lighting layout can be checked for uniformity and quantity of illumination. For larger projects or those with irregular floor plans, lighting design software can be used. Each fixture has its location entered, and the reflectance of walls, ceiling, and floors can be entered. The computer program will then produce a set of contour charts overlaid on the project floor plan, showing the light level to be expected at the working height. More advanced programs can include the effect of light from windows or skylights, allowing further optimization of the operating cost of the lighting installation. The amount of daylight received in an internal space can typically be analyzed by undertaking a daylight factor calculation.
The Zonal Cavity Method is used as a basis for both hand, tabulated, and computer calculations. This method uses the reflectance coefficients of room surfaces to model the contribution to useful illumination at the working level of the room due to light reflected from the walls and the ceiling. Simplified photometric values are usually given by fixture manufacturers for use in this method.
Computer modeling of outdoor flood lighting usually proceeds directly from photometric data. The total lighting power of a lamp is divided into small solid angular regions. Each region is extended to the surface which is to be lit and the area calculated, giving the light power per unit of area. Where multiple lamps are used to illuminate the same area, each one's contribution is summed. Again the tabulated light levels (in lux or foot-candles) can be presented as contour lines of constant lighting value, overlaid on the project plan drawing. Hand calculations might only be required at a few points, but computer calculations allow a better estimate of the uniformity and lighting level.
Different types of electric lighting have vastly differing efficacy and color temperature:
|Name||Optical spectrum||Luminous efficacy
|Incandescent light bulb||Continuous||4–17||2–20000||2400–3400||Warm white (yellowish)||100|
|Halogen lamp||Continuous||16–23||3000–6000||3200||Warm white (yellowish)||100|
|Fluorescent lamp||Mercury line + Phosphor||52–100 (white)||8000–20000||2700–5000*||White (various color temperatures), as well as saturated colors available||15-85|
|Metal halide lamp||Quasi-continuous||50–115||6000–20000||3000–4500||Cold white||65–93|
|Sulfur lamp||Continuous||80–110||15000–20000||6000||Pale green||79|
|High-pressure sodium||Broadband||55–140||10000–40000||1800–2200*||Pinkish orange||0–70|
|Low-pressure sodium||Narrow line||100–200||18000–20000||1800*||Yellow, no color rendering||0|
|Light-emitting diode (white)[failed verification]||Line plus phosphor||10–200||50,000–100,000||Various white from 2700 to 6000*||Various color temperatures, as well as saturated colors||70–85 (white)|
|Induction lamp[failed verification]||Mercury line + Phosphor||70–90||80,000–100,000||Various white from 2700 to 6000*||Various color temperatures, as well as saturated colors||70–85 (white)|
*Color temperature is defined as the temperature of a black body emitting a similar spectrum; these spectra are quite different from those of black bodies.
The most efficient source of electric light is the low-pressure sodium lamp. It produces, for all practical purposes, a monochromatic yellow light, which gives a similarly monochromatic perception of any illuminated scene. For this reason, it is generally reserved for outdoor public lighting usages. Low-pressure sodium lights are favored for public lighting by astronomers, since the light pollution that they generate can be easily filtered, contrary to broadband or continuous spectra.
Main article: Incandescent light bulb
The modern incandescent light bulb, with a coiled filament of tungsten, was commercialized in the 1920s developed from the carbon filament lamp introduced in about 1880. As well as bulbs for normal illumination, there is a very wide range, including low voltage, low-power types often used as components in equipment, but now largely displaced by LEDs.
Main article: Fluorescent lamp
Fluorescent lamps consist of a glass tube that contains mercury vapor or argon under low pressure. Electricity flowing through the tube causes the gases to give off ultraviolet energy. The inside of the tubes are coated with phosphors that give off visible light when struck by ultraviolet energy.
Main article: LED lamp
Light-emitting diodes (LEDs) became widespread as indicator lights in the 1970s. With the invention of high-output LEDs by Shuji Nakamura, LEDs are now in use as solid-state lighting for general lighting applications.
Initially, due to relatively high cost per lumen, LED lighting was most used for lamp assemblies of under 10 W such as flashlights. Development of higher-output lamps was motivated by programs such as the U.S. L Prize.
fluorescent lights mercury vapor excites.